ASG Electric works with you and your utility provider to coordinate all aspects of de-energized services for maintenance of the electrical distribution system.
NFPA 70B, the “Recommended Practice for Electrical Equipment Maintenance,” outlines the requirements for de-energized testing and servicing of electrical components, including both the tasks that must be performed and their frequency. These de-energized tests are a must because they complement your energized preventative maintenance program and improve the overall reliability of your electrical system. Our specialized tools allow us to test circuit breakers, transformers, switchgear and perform cable testing – all according to NETA standards. By comparing the current values against prior maintenance periods, skilled ASG technicians can help you predict and prevent failures.
ASG Electric helps you save money by detecting leaks in your compressed gas & air system.
Ultrasonic testing is a highly-effective tool to detect and identify the leaks in your systems that allow valuable gases and air to escape. Skilled ASG technicians will clearly denote all leaks and determine their respective sizes so calculations can be made to determine the payback for each repair, allowing you to prioritize which leaks are the most critical to fix. For companies using high-cost fuel gases, this service is an easy way to reduce costs and may decrease the safety risk of combustible gases leaking into your facility. The team at ASG will also work with you to determine if any energy rebates are available to offset some of the repair costs.
ASG Electric evaluates your transformer to detect problems, then works to resolve those issues to protect your equipment.
Transformers rely almost entirely on the electrical properties of their windings to operate properly. It is critical to confirm that those electrical properties correspond to the design specifications, meaning the transformer can function as intended. Several testing procedures are available to accomplish this important task. For example, the transformer turns ratio test is able to detect shorts occurring between turns of the same coil, which may indicate inadequate insulation. DLRO testing is performed to measure low resistance and help identify resistance elements that have increased above acceptable values. Finally, the Megger test is used to verify the condition of electrical insulation. ASG technicians can perform all of these tests to ensure that your transformer is safe and reliable.
ASG Electric assesses your facility’s power quality to ensure your electrical system functions at optimum performance.
Without proper power, an electrical device can malfunction or even fail prematurely. It is important to understand variation in voltage, transient voltages, and harmonic content so you can determine how compatible your devices are with your facility’s power quality. ASG will document these power quality issues, review operational integrity or safety issues, and work with you to avoid future problems.
ASG Electric will evaluate your electrical system to determine if it is properly grounded so that a utility overvoltage or lightning strike will find a safe path to earth.
Earth has an electrical property, conductivity (or low resistance), that is used in the electrical systems of your facility. Earth’s resistance is the resistance of soil to the passage of electric current, and the earth is a relatively poor conductor; however, if the area of a path for current is large enough, resistance can be quite low and the earth can be a good conductor.
If there is an instance of overvoltage or lightning strike, you need to ensure that the current will find a safe path to earth. If the current does not find this path, or the ground cannot carry the fault current long enough, the result is potential damage to the equipment inside your building.
There are a few factors that can change the earth electrode requirements from year to year:
- A plant or other electrical facility can expand in size. Such changes create different needs in the earth electrode, and what was formerly a suitably low earth resistance can change.
- As facilities add more sensitive computer-controlled equipment, the problems of electrical noise are magnified. Noise that would not affect older equipment can cause daily problems with new equipment.
- As more nonmetallic pipes and conduits are installed underground, such installations become less and less dependable as effective, low resistance ground connections.
- In many locations the water table gradually falls. In a year or so, earth electrode systems that were effective may end up in dry earth of high resistance.
These factors emphasize the importance of a continuous routine of earth-resistance testing, per NFPA 70B recommenda-tions. It is not enough to check the earth resistance only at the time of installation.
ASG Electric will give the wiring between your utility service transformer and your switchgear a health check.
Testing the wiring / cables between your utility service transformer and your switchgear termination should be part of any electrical predictive maintenance program. Improper installation, or harsh environments can cause damaged or deteriorated insulation, and because of that safety and power reliability can be an issue. The cables are tested with an insulation resistance test using a test meter such as the AEMC Model 5050 Megohmmeter. The test procedure serves as a baseline analysis where future test results can be compared, and assures that cables have not been dam-aged during install, harsh environments, or rodents.
ASG TEGG Services Technicians have been trained on the use of this equipment and proper testing procedures, so they understand that test results:
- are affected by temperature and humidity
- must be property normalized in order to complete a comparative analysis of past test results.
Catastrophic failures with this segment of your electrical system can leave your facility down for several days because of possible damage to the utility transformer and switch gear components.
“Like probably many companies we became aware of the need Lyco Manufacturing Logofor both an arc flash risk assessment and supporting safety procedure. Also like probably many companies we solicited quotes for the work, not entirely sure what we were getting ourselves into. In that process we met Chuck and his team from ASG electric and they quickly differentiated themselves from the rest of the pack [ if you meet them, you will understand what I mean] and we chose them for the project. At every turn, from information sharing, to quality of work, to flexible scheduling, to documentation and last but least employee training this was a top notch effort and I am comfortable in saying that I recommend them highly”.
“I am a PE Electrical engineer and have worked with ASG Electric on many Arc Flash Studies. Specifically, I have worked with the TEGG Pro software used by ASG Electric in the data collection phase in each of these projects. TEGG Pro assures complete an accurate data collection and the various reports allow the engineer to quickly and completely build out the Arc Flash Engineering model”.
Mead-and-Hunt“Compared to other arc flash study projects, where TEGG Pro was not used, the data typically is less organized, the model takes longer to build, and there are more “punchlist” items to review and verify. If I have the opportunity to select the data collection process on a future project, working with ASG Electric and the TEGG Pro software is definitely my first choice”.